SOFTWARE defined networks for smart substations in an active distribution system
AbstractThe Smart Substation (SS) encompasses the characteristics of smart grid, which are increasingly being employed, in the distribution substation of an Active Distribution System (ADS). In order to have effective deployment of a Substation Automation System (SAS), one of the major prerequisites is to have a communication architecture which is being autonomously managed by the employment of Information and Communication Technologies (ICT). Meanwhile, the newly developed technology of Software Defined Network (SDN) is increasingly used in the domain of Smart Grid. This paper explores possibilities for the deployment of SDN in the SAS. This approach has potential to reduce various latencies occurring in message exchanges within an IEC 61850 based SS. Also an algorithm for an SDN controller has been developed to prioritize the time critical GOOSE messages in an IEC 61850 based SS.
IEC 61850 2nd ed, 2013. Communication networks and systems for power utility automation.
Ali, I. Thomas, M.S. Gupta & S. Hussain. S.M.S., 2015. Information modeling for Distributed Energy Resource integration in IEC 61850 based substations, Annual IEEE India Conference (INDICON), New Delhi.
Ali, I. Thomas, M.S. Gupta & S. Hussain. S.M.S., 2015. IEC 61850 Substation Communication Network Architecture for Efficient Energy System Automation. Energy Technology & Policy (2):2381-5639.
Aydeger, A. Akkaya, K. & Uluagac, A. S., 2015. SDN-based resilience for smart grid communications. IEEE Conference on Network Function Virtualization and Software Defined Network (NFV-SDN), San Francisco, CA.
Cahn, A. Hoyos, J. Hulse, M. & Keller, E., 2013. Software-defined energy communication networks: From substation automation to future smart grids. IEEE International Conference on Smart Grid Communications (SmartGridComm), Vancouver, BC.
Dorsch, N. Kurtz, F. Georg, H. Hägerling, C. & Wietfeld, C., 2014. Software-defined networking for Smart Grid communications: Applications, challenges and advantages. IEEE International Conference on Smart Grid Communications (SmartGridComm), Venice.
Zhang, J. Seet, B.C. Lie, T.T. & Foh, C.H., 2013. Opportunities for Software-Defined Networking in Smart Grid. 9th International Conference on Information, Communications and Signal Processing (ICICS), Tainan.
Rinaldi, S. Ferrari, P. Brandão, D. & Sulis, S.,2015. Software defined networking applied to the heterogeneous infrastructure of Smart Grid. IEEE World Conference on Factory Communication Systems (WFCS), Palma de Mallorca.
Pfeiffenberger, T. Du, J. L. Arruda, P. B & Anzaloni, A., 2015. Reliable and flexible communications for power systems: Fault-tolerant multicast with SDN/OpenFlow. 7th International Conference on New Technologies, Mobility and Security (NTMS), Paris.
Irfan, A. Taj, N. & Mahmud, S. A., 2015. A Novel Secure SDN/LTE Based Architecture for Smart Grid Security. IEEE International Conference on (CIT/IUCC/DASC/PICOM), Liverpool.
“Programmable Flow Controller,” http://support.necam.com/SDN/pfv6/download/?id=b5ea21f6-a855-4c50-909d-79de68263e3c
IEC 61850-8-1 ed2.0, 2011. Communication Networks and Systems for Power Utility Automation-Part 8-1: Specific Communication Service Mapping(SCSM) –Mappings to MMS (ISO 9506-1 and ISO 9506-2) and to ISO/IEC 8802-3.
Yalla, M. Adamiak, M. Apostolov, A. Beatty, J. Borlase, S. Bright, J. Burger, J. Dickson, S. Gresco, G. Hartman, W. Hohn, J. Holstein, D. Kazemi, A. Michael, G. Sufana, C. Tengdin, J. Thompsonand, M. & Udren, E.,2002. Application of peer-to-peer communication for protective relaying. IEEE Transactions on Power Delivery (17): 0 885-8977.
Simon, M.S. & Sufana, C.R.,1999. Summary panel discussion: GOOSE [Substation Automation]. Power Engineering Society Summer Meeting, Manhattan, USA.
Zhang, L.X. & Nair, N.K.C., 2008. Testing protective relays in IEC 61850 framework. Australian Universities Power Engineering Conference, Brisbane, Australia.
IEC 61850-9-2 ed2.0, 2011. Communication Networks and Systems for Power Utility Automation-Part 9-2: Specific Communication Service Mapping(SCSM) –Sampled Values Over ISO/IEC 8802-3
IEC 61850-9-2 LE: Implementation guideline for digital interface to instrument transformers using IEC 61850-9-2, UCA International Users Group.
IEC 61850-90-5, 2012. Use of IEC 61850 to transmit synchrophasor information according to IEEE C37.118, IEC Standard.
Bing, H. Xuyang, Z. & Jing, L., 2014. Smart substation precise time research and analysis. IEEE International Symposium on Precision Clock Synchronization for Measurement, Control, and Communication (ISPCS), Austin, Texas.
Kumar, S. Das, N. Muigai, J. & Islam, S. ,2014. Performance evaluation of data transmission in a single and double bus network within the utility substation based on IEC 61850. IEEE PES General Meeting | Conference & Exposition, National Harbor, Maryland.
Sidhu, T. Kanabar, M. & Parikh, P., 2011. Configuration and performance testing of IEC 61850 GOOSE. International Conference on Advanced Power System Automation and Protection (APAP), Beijing, China.